A Canadian chemical plant installed a large heated blower-purge style compressed air dryer, years ago, to condition the instrument air system against freezing temperatures. The dryer selected was oversized for the connected air compressors and had unused on-board energy savings features. A compressed air assessment revealed the site air compressors and compressed air dryers were running inefficiently and causing in-plant pressure problems. Repairs to a compressed air dryer and the replacement of aging air compressors and dryers has reduced compressed air energy costs by 31 percent.
A large fabric mill has implemented an energy management system based on the ISO 50001 standard to track their compressed air system efficiency. As a result of information gained from this system, and measures learned in some recent compressed air training, the company has reduced their compressed air system costs while at the same time achieving increased fabric production output. The savings were gained by not only optimizing the supply side of the system, but by also addressing the end uses.
Technological trends in plastics manufacturing are driving the costs of production down. In industrial PET blow molding specifically, two innovative techniques have had major impacts over the last 15 years: “light weighting” the plastic bottles, and recirculating high-pressure compressed air. Both have helped to improve the energy efficiency of PET blow molding by reducing compressed air requirements dramatically.
PET Power Containers, a Canadian manufacturer of PET plastic containers, had plans for expanding its operations with the addition of more blow-molding equipment. Before the expansion could happen, however, the company needed to assess its compressed air system. Based in Vaughan, Ontario, PET Power provides a dizzying array of differently shaped and sized plastic bottles. Their operations run 24/7, and compressed air plays a key role in their primary manufacturing applications, including PET blow molding, PET preforming, and labeling bottles.
As a reader of this journal, you are well aware that large compressed air systems often have significant wasted air — often from leaks — that represent tens of thousands of dollars of waste per year. However, it is our experience that the so-called “low-cost” measures identified often go un-repaired, while other more costly capital projects get funded. Why? With an ROI of a half year or less, they seem like IQ tests to many compressed air auditors.
After more than 25 years in the compressed air industry, it still amazes me that many plant personnel and even those who sell compressed air products for a living don’t fully understand the relationship between flow, or volume (cfm), and pressure (psig). Walk into many body shops or small manufacturing plants, and you will find the compressor operating at an elevated pressure to satisfy the “demand.” If a plant has low air pressure on the production floor, what is the first thing that the maintenance professional does? You guessed it: He or she “jacks” up the pressure on the compressor, not realizing that he or she made the problem worse.
Replacing air compressors, dryers and filters with more efficient models has saved electrical costs and improved compressed air reliability at the Canada Bread plant in Winnipeg, Manitoba. In addition to this, plant personnel found some additional savings by reducing air leakage and eliminating inappropriate uses. As a result, the plant reduced its compressed air electrical costs by 58 percent and qualified for a utility incentive.
Compressed Air Performance Specialists (CAPS Inc.) is a compressed air consultancy located in Calgary, Alberta. In its most recent compressed air project, the company reduced a 200-hp, multi-compressor system down to a single, 100-hp variable speed drive (VSD) air compressor utilizing 75 hp of compressor energy (kWh), resulting in $70,000 in annual energy savings.
Compressed air audits for chemical and petrochemical plants have many characteristics in common with audits in other industries, but there are some differences in the way these businesses run that impact the goals of the typical audit and how that audit is conducted. In chemical and petrochemical facilities, the reason for auditing the demand side is different than that of other industries. Additionally, there are frequently applications with opportunities for improvement that are not always seen in other industries.
The CertainTeed Gypsum Board plant located in Winnipeg, Manitoba, has renewed their compressed air system and improved their air quality, as a result of information learned at Compressed Air Challenge’s Fundamentals of Compressed Air seminar, some wise choices for new equipment, and thorough investigation of their system. A close look at their distribution system uncovered some surprising results that, once changed, resulted in better system operation. The improvements saved significant operating costs and resulted in a financial incentive from their power utility.
Air System Pressure Influences Compressor Power - Part 3: The Influence of System Pressure on Compressed Air Demand
Energy conservation measures (ECM) associated with compressed air have received a significant amount of attention over the years, mostly due to a reasonably short financial return compared with other energy consuming equipment. Over time many of the corrective actions put forward to reduce compressed air energy consumption have been simplified with the goal of encouraging action. Although this is done with the best of intentions, sometimes simplifications and generalizations do not necessarily lead to positive results. One of the most common energy conservation measures for compressed air that leverages best practice calculations involves reducing system pressure. It is the objective of this series of articles to highlight some of the more common issues associated with estimating energy conservation resulting from changing system pressure.