Industrial Utility Efficiency

# Air Treatment/N2

Just as many ambient air issues with regard to the actual equipment operating environment are created by personnel and can be corrected by personnel, inlet air contamination is always created by humans and there is almost always a correction that will either eliminate the issue or mitigate the effect.

## Heat of Compression: A Major Energy Recovery Opportunity Often Ignored

Often when you mention heat of compression the first thought generally relates to HOC desiccant dryers, which are also an under-applied opportunity for heat recovery. However, there are many other heat of compression recoverable energy savings opportunities in all compressed air and gas systems. This article reviews many opportunities in energy heat recovery and provides answer to commonly asked question.

## Lessons Learned: Saving Energy Costs with Heated Blower Desiccant Dryers

Experienced auditors become wary when they see desiccant dryers installed in customers’ plants. These dryers are required when a plant needs instrument-quality compressed air, or when compressed air piping is exposed to freezing temperatures. However, while desiccant dryers can gain this level of quality, the energy cost of stepping up from a dewpoint of 35 oF to a level of -40 oF increases quite considerably. To attempt to reduce the energy costs of drying to these low levels, heated blower desiccant styles may be used. This article describes three common desiccant dryer types, as well as some experiences, good and bad, with heated blower types.

## Instrument Air and Breathing Air at a Pharmaceutical Plant

A pharmaceutical plant, has had a compressed air assessment performed on two plant systems.  The studies uncovered poor compressed air production efficiency, high air dryer loss, and problems with high flow compressed air uses negatively affecting plant pressure. The plant implemented energy efficiency measures, on the two compressed air systems, saving 46 and 64 percent in energy costs respectively.

## Correctly Solving Low Air Pressure Problems

One of the most common problems in plants is low air pressure. One of the most common solutions is to purchase new air compressors. Often this advice leads to a poor return on investment with the company’s hard-earned money. Often the issues are related to demand, distribution, or both. Solving the wrong problem can be expensive from a capital and operating cost perspective. Determining root cause analysis may cost more up front, but will save tens if not hundreds of thousands of dollars long term.

## Innovative Adsorption Medium for Pressure Swing Desiccant Air Dryers

Compressed air contains contaminants such as dirt, water and oil which must be removed before use. ISO8573.1 specifies air quality classes for these contaminants. Humidity is expressed in terms of Pressure Dew Point (PDP). PDP is the temperature at which air is fully saturated with moisture, when the air temperature falls below this point further condensation will occur.

## Canadian Steel Processor Optimizes Compressed Air at Two Facilities

A steel distribution and processing company has upgraded and consolidated the compressed air systems in two of their distribution and processing facilities for big energy savings. The previous compressed air systems were running in modes of operation with very low efficiency. A complete replacement of the two systems with new air compressors and dryers has reduced the energy consumption significantly.

## Nitrogen, Vacuum and Compressed Air at a Snack Food Plant

This plant has three production lines producing snack food. Depending on the time of year and production demand the plant can operate anywhere from no production lines to all three production lines. A thorough supply and demand-side system assessment was done at this plant. This article will focus on some recommended demand-side reduction projects including nitrogen generation, air vibrators, leaks and vacuum venturis.